ATC utilizes two methods to determine which projects have the potential for economic benefits:
- Stakeholder Input and Analyses
- Reliability Project Screening
These methods are described below.
Stakeholder Input and Analyses
In March 2008, Federal Energy Regulatory Commission (FERC) Order 890-A took effect. As part of this order, FERC requires a coordinated, open, and transparent transmission planning process on both a local and regional level. To comply with these requirements, ATC submitted a compliance filing on Order 890-A that provides a timeline of actions to ensure that the economic planning process is both coordinated and open. ATC has also submitted a compliance filing on Order 1000 that incorporates public policy requirement needs into its economic planning analysis
Annually, ATC will use a process with consistent timelines that combines stakeholder input, historical data, future line flow forecasts, and updated information on the electric system to identify transmission upgrades for economic evaluation.
- During February, we hold an initial stakeholder meeting to review the market congestion summary and potential fixes and to discuss economic study scenarios, drivers, ranges, and assumptions.
- By March 1, we work with stakeholders to request and prioritize new/other economic studies and recommend study assumptions.
- By April 15 – we identify preliminary areas of economic study, study assumptions and models and solicit further comments from stakeholders, including soliciting stakeholders for public policy requirements that drive transmission needs.
- By May 15 – we finalize areas of economic study, study assumptions and models to be used in analysis, including a determination as to why or why not public policy requirements were included in the assumptions.
- By November 15 – we provide a summary of the results of the economic analyses to our stakeholders.
ATC conducts analyses of the projects identified for study over several months’ time and posts the key results, including the extent to which these savings offset project costs. When the expected benefits of a studied project are high enough to justify its costs, the process of developing it as a formal proposal is begun.
As a result of the 2018 ATC/stakeholder collaborative process, we are performing economic analyses on the following ATC facilities:
Economic Planning Study Areas
- Forest Junction – Elkhart Lake 138 kV Area
- Edgewater – Saukville 345 kV Area
Studies will be performed and results shared with stakeholders over the course of the year. In addition, customers and stakeholders who would like to request specific economic studies can do so if they are willing to pay for the studies and are willing to have the results posted publicly.
Reliability Project Screening
Economic analyses were performed on 10 projects from the 2017 10-Year Assessment project list to determine whether those projects were candidates for acceleration or deferral based on economic considerations. Please refer Table EP-1 for the list of projects screened. The list of 10 projects was based primarily on the availability of redispatch and capital costs of the projects; however, lower cost projects specifically identified by the ATC planning department were also included in the study. Generation interconnection and distribution interconnection projects were not eligible for inclusion in this list. Further, capacitor bank projects were not considered since the voltage benefits provided were not captured by the PROMOD software analysis. Finally, projects with in-service dates prior to 2021 were not considered since development of those projects was too far underway to make scheduling changes. As a result of this screening, none of the projects showed significant economic savings to ATC customers. This may change depending on assumptions or modeling of the system. Economic planning will continue to work with reliability planning, if any further analysis needs to be completed.
A similar analysis will be performed in the 2019 10-Year Assessment based upon the 2018 Assessment project list.
|Project #||Project||Planning Zone|
|1||Lakota Rd to Winona 69-kV line convert to 138-kV||2|
|2||Winona - Atlantic 69-kV line rebuild (Winona69)||2|
|3||West Middleton - Stagecoach 69 kV line rebuild (6927)||3|
|4||Gran Grae Substation: Install a second 161/69 kV transformer||3|
|5||Portage - Columbia 138-kV line rebuild (X-13 and X-20)||3|
|6||Portage - Columbia 69-kV line convert to 138-kV (Y-99)||3|
|7||Highway V - Preble 138-kV line uprate||4|
|8||Aviation - North Fond du Lac 138-kV rebuild (G-111)||4|
|9||Bayport area - Pioneer, rebuild as double-circuit 138 kV||4|
|10||Port Washington - Saukville: Rebuild Line 762 to a double circuit||5|