Planning Criteria and tools
New August 29, 2013 – Updated Planning Criteria and Planning Assessment Practices: A copy of our current Planning Criteria can be found here. A copy of our current Planning Assessment Practices can be found here.
The criteria outlined on the web site refers to the version used for the 2013 Assessment.
We employ various system planning criteria to ensure that we develop a reliable and robust transmission system. Our aim with these criteria is to support effective competition in energy markets, to reliably deliver power to systems connected to our system and customers dependent on our system, to provide support to distribution systems interconnected to our system and to deliver energy from existing and new generation facilities connected to our system.
These criteria may be revised from time to time. Situations that could precipitate such a change could include, but are not limited to, new system conditions, extraordinary events, safety issues, operation issues, maintenance issues, customer requests, regulatory requirements and Regional Entity or NERC requirements.
Our planning engineers frequently use the following computer applications to simulate the impact of potential future events on the transmission system. The same applications are used to determine how proposed solutions would address any identified adverse impacts.
|Ventyx PROMOD||predicts the cost of producing energy to serve customers.|
|Burchett Inc. PROMOD Analysis Tool (PAT)||post-processing analytic capability for PROMOD results|
|General Electric MARS||determines “Loss of Load Expectation”, a measure of the ability of system resources to meet customer demand|
|Siemens (PTI) MUST||calculates the capability of the system to transfer power from one area to another while respecting thermal limitations|
|Siemens (PTI) PSS/E||calculates static and dynamic power flows|
|PowerTech VSAT/TSAT/PSAT/SSAT||VSAT calculates the capability of the system to transfer power from one area to another while respecting voltage limitations. TSAT assesses the dynamic behavior of the system under specified condition. PSAT calculates static power flows. SSAT analyzes the small signal stability of the system|
|Power World Corp PowerWorld||calculates static power flows with a visual interface|
|V&R Energy Systems Research POM/OPM||determines “Expected Unserved Energy”, a measure of the ability of the system to deliver resources to meet customer demand.|
Planning Assessment Practices
American Transmission Company generally subscribes to the zone approach to transmission planning assessment using a multi-level planning concept. Diagrams of the planning zones for which regional plans have been developed by ATC are attached in the response to Part 3 of FERC Form 715 and show the existing transmission facilities, 100 kV and above, within ATC’s transmission system.
The concept behind the zone approach to transmission planning is to develop plans that consider all of the needs, limitations and developments within each zone and develop an overall plan for the zone (that is, a plan that emphasizes projects that serve multiple purposes or solve multiple limitations within the zone). In addition, ATC’s transmission planning philosophies incorporate the concept of multi-level transmission planning. When carrying out a comprehensive transmission planning process, consideration must be given not only to transmission needs, zone needs, and ATC-wide needs, but also to plans of other transmission providers. Solutions identified via planning activities within each level are vetted against those in adjacent levels until the most effective overall comprehensive plan is developed. ATC’s planning process will continue to develop the first three levels (individual, zone, ATC-wide). ATC is participating with other Transmission Owners, such as ComEd, DPC, NSP, and ITC, within and affected by the Midwest Independent Transmission System Operator, Inc. (MISO) territory in assessing regional needs.
ATC employs the long-standing practice of using power flow analysis to identify needs and limitations and to evaluate alternative mitigation measures. ATC identifies limitations and needs by simulating non-simultaneous and selected simultaneous outages of each line, transformer, bus section, and generator. ATC does implement operating guides, such as opening lines and bus sections, to mitigate limitations (overloads, low voltages, etc.) during extreme flow conditions.
ATC also conducts dynamic stability analyses within each of its zones to assess the ability of its system to withstand power system disturbances. Many of these analyses have been or are being conducted in conjunction with proposed generation interconnections. Other independent analyses are being conducted to assess dynamic and/or voltage stability performance.
ATC develops transmission projects to address the congestion issues in its footprint and beyond. ATC uses the PROMOD model to analyze congestion across the ATC footprint and surrounding systems and develops projects that will relieve the congestion.
Further, ATC works with neighboring transmission owners, stakeholders and the MISO to develop transmission projects that provide multiple benefits including reliability, economic and public policy benefits. These projects are often more strategic and regional in nature to help provide benefit to multiple areas as well as maintain reliability here in Wisconsin well into the future. These projects are evaluated using traditional reliability planning tools, PROMOD for economic benefits and a combination of traditional FCITC analysis and economic analysis to quantify their public policy benefits.
As part of the MISO, ATC is participating in the MISO Transmission Expansion Plan (MTEP) process. ATC participates actively in all portions of MISO’s planning efforts, including numerous committees and task forces, in regional and economic study efforts and in development of the MTEP.
ATC solicits public and other stakeholder input on the identification of ultimate solutions through its iterative planning process. Projects may be modified as potential solutions listed in this plan are further developed to address the specific needs identified by all stakeholders. The solutions selected to address the needs and limitations identified will reflect the input of transmission planning process stakeholders, including customers, state and local officials, the public, and coordination with other planning processes, to the extent possible.
Specific opportunities for public and stakeholder participation in the planning process are provided in accordance with ATC’s tariff Attachment FF filed at the FERC in response to the portion of FERC’s Order 890 calling for open, inclusive and transparent planning processes. The order was approved conditionally and, after a compliance filing by ATC, it was approved in August 2010. ATC’s Attachment FF covers six separate planning processes and the opportunities stakeholders have to participate in the processes. The six planning processes include:
- Network adequacy planning
- Economic project planning
- Generation-transmission interconnections
- Transmission-distribution interconnections
- Transmission-transmission interconnections
- Transmission service requests.
Provisions include opportunities for stakeholders to provide input to the planning processes in terms of assumptions and projects, provide review of interim results and see final results.
ATC participates in regional transmission assessments conducted by the Midwest Reliability Organization (MRO) Transmission Assessment Subcommittee (TAS), the RFC Transmission Performance Subcommittee (TPS), the MAPP Transmission Reliability Assessment Working Group (TRAWG), the ERAG Reliability Assessments and MISO Reliability Assessments.
In addition to the planning criteria, ATC considers a number of other factors in its transmission planning process. Following is a description of such factors.